Control voltage circuits must be monitored for electrical safety; after all, an undetected electrical fault is as significant as unexpected system downtime and also significantly increases the fire risk. At the same time, unplanned service interventions can be expensive and time-consuming. Some transformer station insurers also demand effective condition monitoring systems. The Bender condition monitoring system gives you a clear overview of all the relevant data for your system.
An uninterruptible power supply (UPS) is used to ensure the supply of critical electrical loads in the event of problems in the power supply. The UPS systems (normally battery or oscillating weight systems) bridge the period until the emergency power systems (generators) are activated or the network is available again. Electrical safety is continuously monitored by Bender products, including offline monitoring.
The VMD258 analogue voltage relay monitors three-phase AC systems for under and overvoltage (window function). It does not need a neutral point connection and is therefore suitable for all 3AC systems. The supply voltage of the electronics is taken from the system to be monitored. The supply for the electronics, the relays and the connection for the external energy store are separated from the system with dual insulation. Special input transformers muffle the transfer of interference factors from the system. The response values for under and overvoltage and for response delays can be adjusted to any level.
|Product Overviews||Power Quality/Measuring and monitoring relays||2.7 MB||EN||2022/05/25 08:08:0925.05.2022 08:08:09|
|Product Overviews||Product Overview ISOMETER®/ISOSCAN®||5.4 MB||EN||2023/11/14 06:12:1314.11.2023 06:12:13|
|Product Overviews||Product Overview - Residual Current Monitoring||6.2 MB||EN||2023/11/09 12:42:5309.11.2023 12:42:53|
|Flyer||Power Quality||468.0 KB||EN||2022/12/14 08:20:2814.12.2022 08:20:28|
|Market Segment Brochures||Power Plants||3.8 MB||EN||2021/04/15 12:34:2215.04.2021 12:34:22|
|Application note||EDS309x||1.4 MB||EN||2019/05/13 10:30:3813.05.2019 10:30:38||D00012|
|Technical article||Insulation Fault Location - Planning and Setup||112.4 KB||EN||2019/05/13 10:29:2213.05.2019 10:29:22|
|Technical article||Electrical Safety in Control and Auxiliary Circuits||632.6 KB||EN||2019/05/13 10:29:2213.05.2019 10:29:22|
|Technical article||Where Residual Current Technology Meets the IT System||353.8 KB||EN||2019/05/13 10:29:2213.05.2019 10:29:22|
Measuring relays and protection equipment - Part 1: Common requirements
Measuring relays and protection equipment - Part 127: Functional requirements for over/under voltage protection
Safety requirements for secondary batteries and battery installations - Part 2: Stationary batteries
Electrical safety in low voltage distribution systems up to 1 000 v a.c. and 1 500 v d.c. - Equipment for testing, measuring or monitoring of protective measures - Part 8: Insulation monitoring devices for IT systems.
Electrical safety in low voltage distribution systems up to 1000 V a.c. and 1500 V d.c. - Equipment for testing, measuring or monitoring of protective measures - Part 9: Equipment for insulation fault location in IT systems
Electrical safety in low voltage distribution systems up to 1000 V ac and 1500 V dc - Equipment for testing, measuring or monitoring of protective measures - Part 15: Functional safety requirements for insulation monitoring devices in IT systems and equipment for insulation fault location in IT systems